The inverter generates an ace supply from its dc power source, which is fed into a step-up transformer. The primary function of the transformer is to increase the inverter AC voltage to that required by the load.
The transformer also protects the inverter from weight disturbance, whilst also providing galvanic isolation (a way of separating input and output).Contemporary inverter models use IGBTs (Insulated Gate Bipolar Transistors) rather than more conventional switching components. You can go through this link http://www.thesunpower.co.th/ to get info about Uninterruptible Power Supplies.
IGBTs incorporate the fast- high and performing power capacity for the Bipolar Transistor using the voltage control characteristics of a MOSFET gate to create a versatile, high-frequency switching device. This, in turn, has given rise to reliable, efficient and better inverters. Transformer-based UPS will also be given a dual input solution as standard, which is often chosen at installation by simply removing a linking connector from its input terminal. You can choose the best STS via visiting http://www.thesunpower.co.th/productslist.aspx?CategoryID=26&selection=7
This enables it to be operated from two separate AC supply resources thus adding further resilience. A transformerless UPS might be installed with dual input capability, with materials derived from the exact same origin, but this is generally a manufacturer-healthy solution.
The primary goal behind the release of transformerless units was to lessen the overall physical size and fat thus creating an uninterruptible power system more desirable for smaller installations and/or computer room/office-type conditions, where space may be limited. Additionally, it provides far less noise and heat than its transformer-based relative and contains far lower input harmonic distortion levels rendering it compatible with environments where digital equipment (such as computers) may be more vulnerable to this type of distortion.
In the place of the step-up transformer, a transformerless UPS runs on the staged procedure for voltage conversion. The initial stage includes a rectifier and booster converter to build a dc source for your inverter. An uncontrolled, three-cycle bridge rectifier converts the AC offer into a power voltage. That is passed through a mid-point booster signal to step the dc voltage around generally 700-800Vdc that a battery charger and inverter are driven.